From inside (document excerpt):
10,000W Generator Topic Limited Warranty Safety Guidelines General Precautions Controls Pre-Operation Check Operation Servicing Maintenance Transporting/Storage Assembly Compliance Specifications Parts Listing Page 3 5 6 15 18 19 21 22 29 30 32 33 34 WARNING! READ AND UNDERSTAND ALL SAFETY PRECAUTIONS IN THIS MANUAL BEFORE OPERATING. FAILURE TO COMPLY WITH INSTRUCTIONS IN THIS MANUAL COULD RESULT IN PERSONAL INJURY, PROPERTY DAMAGE, AND/ OR VOIDING OF YOUR WARRANTY. ALL-POWER WILL NOT BE LIABLE FOR ANY DAMAGE BECAUSE OF FAILURE TO FOLLOW THESE INSTRUCTIONS.
2 Owner’s Manual Controls (cont) Switch Position The voltage selector switches the main power carrying windings of the generator to produce 120V ONLY or 120/240V. 120V ONLY: ONLY the 120V receptacles can be used. Do not use the 120/240V receptacle in this position. The most power will be available at the 30A 120V locking plug receptacle. This unit does not have a voltage select switch. AC Applications Before connecting an appliance or power cord to the generator: · Make sure that it is in good working order. Faulty appliances or power cords can create a potential for electrical shock. · If an appliance begins to operate abnormally, becomes sluggish or stops suddenly, turn it off immediately. Disconnect the appliance, and determine whether the problem is the appliance, or if the rated load capacity of the generator has been exceeded. · Make sure that the electrical rating of the tool or appliance does not exceed that of the generator. Never exceed the maximum power rating of the generator. Power levels between rated and maximum may be used for no more than 30 minutes. NOTE Substantial overloading will open the circuit breaker. Exceeding the time limit for maximum power operation or slightly overloading the generator may not switch the circuit breaker OFF, but will shorten the service life of the generator. 17 Owner’s Manual Operation Pre-Operation Check 1. Remove the oil filler cap and wipe the dipstick clean. 2. Check the oil level by inserting the dipstick into the filler neck without screwing it in. 4. If the level is low, fill to the top of the oil filler neck with the recommended oil. OIL FILLER HOLE OIL FILLER CAP UPPER LEVEL Fuel Check the fuel gauge, and refill the tank if the fuel level is low. Make sure it has at least 3 gallons of fuel before starting your new generator. Refuel carefully to avoid spilling fuel. Do not fill above the shoulder of the fuel strainer. WARNING Gasoline is highly flammable and explosive, and you can be burned or seriously injured when refueling. · Stop engine and keep heat, sparks, and flame away. · Refuel only outdoors. · Wipe up spills immediately. Fuel tank capacity: 30L 8 galllon FUEL GAUGE FUEL STRAINER SHOULDER FUEL FILLER CAP 19 10,000W Generator Assembly Battery Installation 1. Remove the cover under the panel as shown. 2. Screw on one bolt to rivet the battery and screw the bolts to close up the plate as shown below. Rive t b a t t e ry Clo se u p t h e p la t e 30 10,000W Generator Compliance UNITED STATES ENVIRONMENTAL PROTECTION AGENCY, WASHINGTON, DC 20460 2007 Model Year Certifcate of Conformity · Manufacturer: Chongqing Dajiang Power Equipment Co. Ltd. · Certificate Number: CDP-NRSI-07-01 · Effective Date: 5/31/2006 · Date Issued: 5/31/2006 Merrylin Zaw-Mon, Director, Compliance and Innovation Strategies Division, Office of Transportation and Air Quality. Pursuant to Section 213 of Clean Air Act (42 U.S.C. section 7547) and 40 CFR 90, and subject to the terms and conditions prescribed in those provisions, this certificate of conformity is hereby issued for the following small non-road engine family, more fully described in the documentation required by 40 CFR 90 and produced in the stated model year. This certificate of conformity covers only those new small non-road engines which conform in all material respects to the design specifications described in the documentation required by 40 CFR 90 and which are produced during the model year stated on this certificate. This certificate of conformity does not cover small non-road engines imported prior to the effective date of the certificate. SMALL NON-ROAD ENGINE FAMILY: 6CDPS This certificate of conformity is conditional upon compliance of said manufacturer with the averaging, banking, and trading provisions of 40 CFR Part 90, Subpart C both during and after model year production. Failure to comply with these provisions may render this certificate void ab initio. The HC + NOX family emission limit (FEL) is: g/k W-hr. It is a term of this certificate that the manufacturer shall consent to all inspections described in 40 CFR 90.126 and 90.506 and authorized in a warrant or court order.